The best orientation of the equipment power lead equipment in the purification workshop is to walk towards the wall, because this is the shortest distance between the power lines, and the equipment is also best to lean against the wall or close to the wall. All electrical panels, controllers, distribution equipment and starters, and components that do not require daily use in the purification workshop, should be equipped in areas without cleaning constraints.
The material quality of cable pipeline should be determined according to the type of building. For example, in building with block wall, galvanized metal pipeline can be used in indoor cable pipeline. The wires in the plug-in assembly should be heavy-duty wires, and overload maintenance equipment should be installed. The plugs must be designed with sealing equipment to seal dust and moisture so as to ensure cleanliness and hygiene.
The power sockets in the purification workshop should be equipped with embedded devices so as to eliminate the crowds and cracks, facilitate cleaning, and should be waterproof and damp-proof; switches and sockets should be equipped at a practical height above the floor, such as when the water pipe washes the floor, they should not be affected; sufficient spare sockets should be installed in the room to meet the needs of future expansion of production; and the light switch should be equipped as far as possible outside the purification workshop.
The personnel in the purification workshop need to communicate with the managers outside, so communication equipment is necessary. Communication equipment should be equipped with audio control system which can be sterilized and installed flat in the wall or window, including broadcasting system, intercom system and telephone system. The telephone should be waterproof, without dial or button, and can be hung in niches. Poor conditions can be installed in boxes on walls. In order to ensure the safety of the workshop, certain alarm equipment should be set up, and fire detectors in the form of temperature, light and smoke should be set up alone or in combination.
In the purification workshop, in order to reach the required cleanliness level, a lot of circulating air is usually used. Therefore, it is sometimes impossible to fully explore the occurrence of fires only by installing prospectors on the roof. Therefore, it should be added according to the air flow condition. Perhaps it should be considered to install smoke sensor in the return air outlet for useful exploration of fires.
Thank you for reading, this article source: Chinese decoration design more content and questions please click: we will continue to work hard to provide you with services, thank you for your support!